|View Issue Details [ Jump to Notes ] ||[ Issue History ] [ Print ] |
|ID||Project||Category||View Status||Date Submitted||Last Update|
|0000095||Hall D Online||Controls||public||2011-06-24 10:41||2011-12-15 13:38|
|Assigned To||ballard|| |
|Summary||0000095: HMI Control interruptions from Ethernet outages|
|Description||During the coil tests we had several outages of HMI Control that could only resolved by rebooting both the HMI Server computer and the RSLinx Enterprise server. |
I did some testing and identified that when I disconnected and reconnected the network cable from halldsc5 (the HMI Server), communication between halldsc5 and halldsc2 (RSLinx Enterprise server) was permanently lost. This was only noticed because I could not ping from halldsc5 to halldsc2.
We need to test this again with the real network hardware and HMI computers.
|Additional Information||Enclosed is the transcript of the testing I performed on 23 June 2011 in the Test Lab.|
|Tags||No tags attached.|
|Work by outside group for Hall D||No|
|Attached Files|| Ethernet Troubleshooting.txt [^] (2,446 bytes) 2011-06-24 10:41 [Show Content]